MK-R — Reactor
MK-R is designed to accommodate current-limiting and arc…
MK-R is designed to accommodate current-limiting and arc suppression reactors. Installing reactors in substations increases the overall reliability of the network.
MK-R consists of one or several modular units, joined into a single building, in which the installation of reactors and control panels is performed.
A feature of the installation of reactors is the heating of the metal structures of the building in short-circuited circuits, therefore, in the manufacture of buildings for the installation of high-current reactors, special conditions must be met to reduce interference.
In MK-R, depending on the technical task, electric heating, working lighting, emergency lighting, repair lighting, lighting of entrances, outlet networks, ventilation designed for assimilation of excess heat, air conditioning, OPS, ACS, SCS networks, video surveillance are carried out, and cables and wires of internal connections for auxiliaries of the premises.
The main lighting of MK-R is made by LED lamps, emergency — by LED lamps with a battery or LED AC / DC lamps.
Heating MK-R is carried out by electric heaters located along the walls of the blocks. Heating control — manual and automatic.
MK-R is equipped with natural or mechanical inlet ventilation and forced mechanical exhaust ventilation.
The MK-R is equipped with a 220 / 380V, 12V (24,36,42) socket network for repair lighting, a structured cable network.
The security and fire alarm system is based on magnetic contact sensors installed on the gates and doors of the building. When performing an access control system, the doors and gates are additionally equipped with an electromagnetic lock. The premises are equipped with smoke and heat detectors, glass break detectors, volumetric detectors, exit buttons and a manual call point. Outside the building, a «Siren» sound notification and a reader for disarming are installed. A fire alarm panel is provided with a control panel installed inside, a control panel, a switching device. The sensors are connected to the security and fire alarm devices with a fire-resistant cable.
At the request of the Customer, a video surveillance system based on stationary cameras and a video surveillance cabinet with installed equipment for storing and transmitting data is mounted in the building.