MK-CHRP frequency converter building
MK-VRP is necessary to regulate the frequency of…
MK-VRP is necessary to regulate the frequency of the voltage. The main area of application of these devices is to change the speed and torque of asynchronous electrical machines. The principle of operation of control and regulation is based on the dependence of the rotation speed of the magnetic field on the frequency of the supply voltage.
MK-ChRP consists of one or several modular units, joined into a single building, in which the equipment is installed.
In MK-CHRP, depending on the terms of reference, electric heating, working lighting, emergency lighting, repair lighting, entrance lighting, outlet networks, ventilation designed for assimilation of excess heat, air conditioning, fire alarm system, ACS, SCS networks, video surveillance are performed, and cables and wires of internal connections for auxiliaries of the premises.
The main lighting of MK-ChRP is made by LED lamps, emergency — by LED lamps with a battery or LED AC / DC lamps.
Heating MK-ChRP is carried out by electric heaters located along the walls of the blocks. Heating control — manual and automatic.
MK-CHRP is equipped with natural supply ventilation through air dampers and forced mechanical exhaust ventilation, or a supply and exhaust unit with filtration and heating of supply air. Air recovery in the ventilation system is possible. Installation of air conditioners is possible in MK-ChRP to create a microclimate.
In MK-ChRP, a 220 / 380V, 12V (24,36,42) socket network is installed for repair lighting, a structured cable network.
The security and fire alarm system is based on magnetic contact sensors installed on the gates and doors of the building. When performing an access control system, the doors and gates are additionally equipped with an electromagnetic lock. The premises are equipped with smoke and heat detectors, glass break detectors, volumetric detectors, exit buttons and a manual call point. Outside the building, a «Siren» sound notification and a reader for disarming are installed. A fire alarm panel is provided with a control panel installed inside, a control panel, a switching device. The sensors are connected to the security and fire alarm devices with a fire-resistant cable.
At the request of the Customer, a video surveillance system based on stationary cameras and a video surveillance cabinet with installed equipment for storing and transmitting data is mounted in the building